CAN ULC S536 PDF
CAN/ULC-S PERIODIC INSPECTIONS AND TEST – DAILY AND MONTHLY. NOTE: Refer to Appendix D for examples of Inspection and Test Record. SCOPE. This Standard provides requirements for the inspection and testing of fire alarm systems and specifies the devices and functions to be inspected. 1 SCOPE This Standard prescribes requirements for the inspection and testing of fire alarm systems and specifies the devices and functions.
|Published (Last):||18 June 2012|
|PDF File Size:||20.52 Mb|
|ePub File Size:||9.99 Mb|
|Price:||Free* [*Free Regsitration Required]|
Free from mildew, cuts and deterioration? Low temperature supervisory device tested. F Confirm that the alarm transmission to the fire signal receiving centre is received.
Low Pressure supervisory device inspected and tested.
Standards Council of Canada
These are the units that provide an interconnection to conventionally wired devices like manual pull stations, sprinkler isolation valves, flow switches, low air and the like; If your system employs a UDACT communicator, the technician must ensure that appropriate signals generated by the system during the testing must be received at the monitoring station; Ilc addressable relay modules must be listed on the Individual Device Test Recordand their locations and function documented.
Monthly Inspection and Tests A Pilot lights are functioning? T Output circuit alarm indicators operate. Hose Connection Pressure Reducing Valves: Zone of each alarm initiating device is correctly printed.
Minor leak at no flow? It’s a good idea to check the battery compartment every six months for leakage or corrosion on the terminals.
CAN/ULC-S | Standards Council of Canada – Conseil canadien des normes
O Emergency telephone verbal communication operates. Is an AC disconnecting switch installed? V Visual indicator test lamp test operates. For more information you can email us or telephone Are above results comparable to previous tests?
Most smoke detectors installed today are wired directly to dan household electrical system. Gauges to ensure good condition and normal pressure? Backflow prevention assemblies have been tested by an agency acceptable to the local authority? These units are vulnerable to electrical failures they won’t function in the absence of power.
Yes No Time for motor to accelerate to full speed: Confirm field device free of damage. Individual alarm and supervisory input zone clearly indicated and separately designated. While in standby mode, voice communication busses used for paging, alert signal, alarm signal, and emergency telephone communication circuits, an Q open circuit fault, or short circuit fault, or operation of an overcurrent protective ulx provided for the purpose, shall result in a specific trouble indication specific to the faulty buss.
The fire signal receiving centre is ULC Listed. All addressable devices must be individually listed on the Device Test Record sheet. While advances continue to be made in the technology, the need for maintaining proper testing records becomes even more important. Yes No NA Belt checked for proper tension? All parts valves, hoses and fire extinguishers accessible?
Hydrostatic test at not less than Individual alarm and supervisory input zone designation labels are properly identified. Magnetic door holder release activated by fire alarm system?
Zones or module numbers if the system being tested is addressable must be recorded for each field device on the Individual Device Test Record ; End-of-Line devices resistors – these have to be listed along with their locations on the Individual Device Test Record and specific testing must be upc that requires their physical dismounting and re-installation; Cna data buss, power buss, and in-suite signal isolators – these have to be listed on the Individual Device Test Record including a reference to their actual location and some may require physical dismounting in order to affect a proper test; Smoke detector sensitivity readings – results must be recorded on the Individual Device Test Record.
Valve supervisory switches indicate movement? Powered independently of the fire alarm control, these devices are normally not connected to it. J Upon failure of one amplifier, system automatically transfers to backup K amplifier s. D B Terminal connections clean? Fire Alarm System Inspection Services. Reduced pressure assembly valves inspected for leaks or corrosion?
Cooling water level is normal Inspect exhaust hangers and supports? For detectors that cannot be properly tested, your local authority may require you to initiate a replacement program where a certain number of detectors are upgraded automatically every x536. Full operation of adjustments such as pattern selection? This document has been provided to the building owner or their authorized representative who has acknowledged receipt of same below. Alarm signal manual silence operates. Fire shutter release activated by fire alarm system?
Once a month or so, take your vacuum on it’s lowest setting and utilizing a soft brush attachment, clean out the vents of the detector. Output circuits for selective voice paging, including visual indication, F operates.