CRABTREE LOADSTAR MCB PDF
Used But Good Condition. Crabtree Loadstar Range MCB. Early Style Series 2 Approx – Crabtree Loadstar MCB 20 Amp Single Pole Breaker Type B 20A . Product Description. Crabtree Loadstar 6HS16C C Type 16A Single Pole Mcb. 6HS16C is a 16A out going MCB for Crabtree Loadstar commerial/industrial. Product Description. Crabtree Loadstar 6HS16B B Type 16A Single Pole Mcb. 6HS16B is a 16A out going MCB for Crabtree Loadstar commerial/industrial.
|Country:||Republic of Macedonia|
|Published (Last):||10 November 2005|
|PDF File Size:||4.31 Mb|
|ePub File Size:||11.51 Mb|
|Price:||Free* [*Free Regsitration Required]|
Again thank you all for your help. OP have you tried to remove the breaker?
Crabtree Loadstar MCB 10 Amp Single Pole Breaker Type B 10A 6FS10B Series 1
Does not see daylight! I am still intrigued as to why it cmb knocking off the RCB as absolutely nothing has touched the cable and the run from the cu to the the adjoining shed is all indoors. Your name or email address: Maybe the MCB has another circuit connected to it.
This is after I toggled mcb switch a dozen times! You should find water problems in at least one of them. Agree it won’t is highly unlikely! It is a Loadstar.
Hi spinlondon thanks cable fully enclosed. Else, yes, just drop the busbar, lift out the mcb, drop new one in and refit busbar.
Crabtree Loadstar 6HS16B B Type 16A Single Pole Mcb – Your Electrics | Electrical Supplies
Share This Page Tweet. Mcv I think I was barking up the wrong tree with my mcb hard fault! Yes, my password is: I now need to replace a suspect mcb Looking at the photographs of the cu can you tell me if I need to undo the bottom screw of every mcb in that sector to take off the copper neutral bus bar before I can take out the suspect mcb by pulling down the back release ring on the mcb etc.
Rcd still tripped immediately whenever mcb was switched on. Alun Tom and unphased like this.
As other poster said that aint the neutral bar it is the LIVE busbar. Its not, JP, they have special shrouded busbars and a single tab lock-in system unique to the Starbreaker. BazzaApr 26, Placed a light attachment to one crabtreee the sockets and all was well for some 5 or so hours.
Unusual for an MCB to fail, are you sure its not overloaded. Yes my fault re polarity of bus bar!!
You would spend more lucrative time just visually inspecting all your garden stuff. The circuit in question needs meggering, doesn’t sound loaestar an mcb problem to me.
Crabtree Loadstar consumer unit. Changing mcb | Screwfix Community Forum
Do you already have an account? To do this you loaadstar also need to remove the neutral of the suspect circuit. Now only the 2. The screw is already loose. I am glad you corrected me on that issue! RCD trip due to there being a difference in the current going out through the live and the current returning through the Neutral.
Alun TomApr kcb, For the MCB to be the cause, there would have to be a path for the lost current to take. Alun Tom likes this.
Crabtree Loadstar MCB 20 Amp Single Pole Breaker Type B 20A 6M1B20 Series 2
I have a Crabtree Loadstar cu that was installed some five years ago. The loadsyar is just one twin and earth going directly from mcb to a twin 13a socket which has now been disconnected! Yes odd I know! You must log in or sign up to reply here.
Not likely to be mcb at fault.